There are three criteria at the bottom
of the SYSMATRIX TR design solution:
Rolled steel side sections and “roof-bottom” weld fabricated structure are the two special features that form the framework of the wiring closet.
The assembly is so easy, almost on an instinct level and the parts are precisely standardized so much so that you could probably do without the Assembly Manual.
Try and assemble the telecommunications closet and you’ll relive the childhood joy, when you used to assemble the models from the tinker toys with your own hands.
We believe you’d like it!
AIR CONTROL SYSTEM - double zone control and management system.
The AIR CONTROL SYSTEM ensures:
Powerful modern active equipment, generates a huge amount of heat, can negatively affect the stability of the system performance.
In order to remove the warm air streams from the cabinet interior space we HAVE ALREADY installed four 120mm (440 cubic meters/hour) vent elements into the cabinet roof.
One more reason you would like to choose SYSMATRIX cabinets in your projects is a flat compact packaging!
It is convenient for both: storage and moving.
The construction is supplied unassembled and this allows for between 50% and 70% savings of total space!
Three Undisputable Advantages:
1. Saving between 50% and 70% of the rack space during its storage and transportation.
2. Assembled construction allows for delivery and mounting the rack at the technical facility with narrow doorways and/or no cargo elevators.
Telecommunication server rack SYSMATRIX TR-series is the best solution to place telecommunications equipment and organize communication centers.
The set is supplied in a flat and compact package which is a profitable option when transporting ore storing. Installation is easy and simple.
The active ventilation and Air temperature control system is included in the base model. All cable entries are equipped with brush strip panels and cable managers.
The telecommunication server rack is supplied with heavy duty rolling casters equipped with a “brake” option to facilitate mobility.
To remove hot airflow from the working space, there is a 4 active-fan panel factory installed on top of the rack with a capacity of 440m3/h.
Thanks to a flat compact packaging, a server rack TR-Series can save up to 50%-70% on transport and storage.
Assembling construction allows delivering and mounting a rack in tight rooms with narrow doorways access without cargo elevators.
Now, just one technician could deliver a server rack without special transport and tools.
AIR CONTROL SYSTEM guarantees:
• maximum performance of IT equipment in secure temperature regime
• reduced electricity costs;
• increased lifetime of active ventilation;
• reduction in noise .
3 types of doors:
• Glass in metal frame with perforation;
• Perforated metal;
• Solid metal Framework:
• Prefabricated profile sections
• Top and bottom have dust-tight brush panels with cable managers
• Passive – convection heat flow due to perforation of front and rear doors
• Active – by setting in the top fan module (all models)
• IP41: glass/perforated sash
• IP20: perforated door
• Static load not exceeding 1800 lb.
•Rolled steel profile
• Frame thickness: 2 mm, 19” profiles 2mm, other components parts; 1.5mm
• Powder paint with degreasing and anticorrosive phosphate
• Grey: RAL7035
• Base model includes:
set of doors,AIR CONTROL SYSTEM, active ventilation,
side panels, 2 pairs (front & rear) 19” profiles, brush strip plate,
rolling casters and 4 legs, a set of nuts, bolts, washers and screwdriver.
Setting the skeleton. Using KIT A, combine bearing profiles 1 , top 2 and bottom 3 in one single carcass. Do not tighten the bolts at this point.
Install wheels and adjustable feet onto the bottom panel.
Setting the external medium horizontal beams. Only applicable for 33U, 37U, 42U racks. The external medium horizontal beam is to be installed between 2 side panels on each side. To determine the height, it is necessary to set a side panel onto the carcass and put the horizontal beam on top of the panel. That will be the correct position. You can now screw the beam using the KIT B and remove the panel. Do the same on the other side of the carcass.
Setting the internal medium horizontal beams. Only applicable for 33U, 37U, 42U racks. Using the mounting KIT B, install the internal horizontal rail at the same height as the external one.
Setting the upper and lower internal horizontal beams. To set the upper and lower internal horizontal beams, it is necessary to place a beam against the 4th, 5th and 6th holes of the front and rear bearing profiles. Install it, using KIT B. Do the same with lower horizontal rails. Do the same on the other side of the carcass.
Installing the dowels pins, fixing the side panels.
Installing the side panel latch parts. Using the KIT B fix side panel latch catch as shown. 2 for each side panel.
Installing vertical mounting rails
U-mark.Using KIT C, install the
vertical mounting rails onto
the internal horizontal
beams, installed earlier
(Step 4, 5). Make sure the
oval holes of the vertical
mounting rails match
square holes on each
horizontal rail. Do the same with
the other mounting rails.
If needed, the depth
can be adjusted shifting the rails.
You can tighten all elements of the Rack now.
Installing front and back door. Preinstall the front and back door hinges onto the carcass, according the picture. Install the front and back door handle and latch lock. Install the door.
Fasten side panels.
|Types of produced sizes||
|Three types of door||
|Protecting by IP||
Base case system includes a set of doors, a set of side panel, 2 parts of 19’ profile,eye bolts. Bottom parts are supplied with a dusttight hatch for cable input, adjustable legs or 4 wheels, a set of nuts/screws/washers (50un).
|Marks||Descriptions||Package (CTNS)||G.WT (KGS)||Meas (CBM)|
|TR 6618.***||19" cabinet for IT 18U 600x600x930||4||59,7||0,19|
|TR 6818.***||19" cabinet for IT 18U 600x800x930||4||69,3||0,23|
|TR 6018.***||19" cabinet for IT 18U 600x1000x930||4||75,9||0,27|
|TR 6622.***||19" cabinet for IT 22U 600x600x1100||4||66,6||0,21|
|TR 6822.***||19" cabinet for IT 22U 600x800x1100||4||76,8||0,25|
|TR 6022.***||19" cabinet for IT 22U 600x1000x1100||4||87||0,29|
|TR 6627.***||19" cabinet for IT 27U 600x600x1335||4||75,4||0,22|
|TR 6827.***||19" cabinet for IT 27U 600x800x1335||4||86,5||0,27|
|TR 6027.***||19" cabinet for IT 27U 600x1000x1335||4||97,6||0,32|
|TR 6633.***||19" cabinet for IT 33U 600x600x1605||4||86,5||0,25|
|TR 6833.***||19" cabinet for IT 33U 600x800x1605||4||99,4||0,30|
|TR 6033.***||19" cabinet for IT 33U 600x1000x1605||4||112,3||0,35|
|TR 6637.***||19" cabinet for IT 37U 600x600x1790||4||93,8||0,27|
|TR 6837.***||19" cabinet for IT 37U 600x800x1790||4||104,9||0,31|
|TR 6037.***||19" cabinet for IT 37U 600x1000x1790||4||116||0,35|
|TR 6642.***||19" cabinet for IT 42U 600x600x2010||4||102,5||0,31|
|TR 6842.***||19" cabinet for IT 42U 600x800x2010||4||115,8||0,34|
|TR 6042.***||19" cabinet for IT 42U 600x1000x2010||4||129,1||0,37|
|TR 6647.***||19" cabinet for IT 47U 600x600x2230||4||107,5||0,43|
|TR 6847.***||19" cabinet for IT 47U 600x800x2230||4||119,5||0,49|
|TR 6047.***||19" cabinet for IT 47U 600x1000x2230||4||131,5||0,55|
For drawing up of design documentation provide drawings in DWG format.
Nowadays, the modern server equipment
is much faster and more powerful than in the past.
As a result, a lot of
heat is generated in working space which can affect the performance of whole
system, unfortunately, in negative way.
That is why, one of the most important
factors impacting the life and reliability of high-priced equipment is the
temperature regime in a server rack.
Moreover, most of servers are integrated
in public and office environment, were the non-stop cooling fan noise prevents
focusing on accomplishing work,
but overheating of the server equipment can cause system crushes and even data loss.
– the automatic
control of ambient temperature regime and active ventilation in server racks.
device reads off two temperature gauges, installed in different areas,
engages 4 fan cooling panel running only when the temperature surpasses the
save operating limit.
The Air Control
board is installed into the top of the rack, which save 1U internal space.
AIR CONTROL SYSTEM :
The control unit has three types of modes:
While pressing and hold the SET button, it switches to adjustment mode. Hold down the SET button more than 3 seconds, reset to factory default settings. A single press button SET in regulatory regimes or initialization switches to the operating mode. Use the UP- button and DOWN- button to modify the selected parameter.
|F1||A channel temperature setting||.-19,9C +99,9C||12,0||Press and hold the SET button to select the setting temperature. Use the up and down set temperature value. Short press SET to set the default settings|
|F2||A channel temperature hytersis||1,0C - 20,0C||2,0||Press and hold the SET button to select the setting range of operation. Use the up and down button peak value. Short press SET to set the default settings|
|F3||B channel temperature setting||.-19,9C +99,9C||12,0||Press and hold the SET button to select the setting temperature. Use the up and down set temperature value. Short press SET to set the default settings|
|F4||B channel temperature hytersis||1,0C - 20,0C||2,0||Press and hold the SET button to select the setting temperature. Use the up and down having set the temperature value. Short press SET to set the default settings|
|F5||Temperature correction||-10+10||0,0||The calibration function (correction) of reading between the actual temperature and the determined unit|
|F6||Start-up delay||0-5||2,0||Press and hold the SET button to select the setting delay. Use the up and down to set the desired value. Short press SET to set the default settings.|
|E1||A channel error||A channel self-testing error|
|E2||B channel error||B channel self-testing error|